1.1 Use of the Manual
This manual describes the FHCT floor heating system — how to design the room, select the product, and install the system. It is important to thoroughly review this manual and the following document prior to installation:
Thermostat Installation and Operation Manual
For additional information regarding any aspect of the FHCT System, contact:
1.2 Safety Guidelines
The safety and reliability of any floor heating system depends on proper design, installation, and testing. Incorrect installation or mishandling of the product can cause damage to the heating cable, system components and property, and can create a risk of fire or shock. The guidelines and instructions contained in this guide are important. Follow them carefully to minimize these risks and to ensure that the FHCT system performs reliably.
1.3 Remember to measure resistance
The resistance should be measured between the two conductors, blue and brown. Compare this resistance reading to the resistance specified in the Product Selection “Table 1”. The value should be within -5%～+10%. If you get a different reading, contact Xuhui at 86-553-7477605.
Also, measure the resistance between the blue, brown and shielding/ground wire. Both should read infinity. If you get a different reading, contact Xuhui at 86-553-7477605.
Please refer to “5 Commissioning” for instructions on how to measure the resistance.
1.4 25-year Limited Warranty
For a period of twenty-five (25) years from the date of purchase Xuhui warrants that the FHCT heating cable is free from defects in material, design and workmanship. The extended warranty is only valid if the warranty certificate has been properly completed and mailed, and the installation is in accordance with the installation instructions.